LE3U PLC is compatible with Mitsubishi GX-Developer/GX-WORK2 software and supports human-machine interface connection, making it equivalent to the Mitsubishi FX3U PLC.
It supports ladder programming, download, and monitoring, and uses a programming port for program download and communication with the human machine.
The LE3U PLC is designed with an industrial-grade 32-bit MCU, which has strong anti-interference capabilities and runs much faster than the FX3U PLC.
The transmission baud rate for the LE3U PLC is 38400.
- Support Mitsubishi GX-Develoer\GX-WORK2
- Support for human-machine interface connection, the application is completely equivalent to Mitsubishi FX3U
- Support ladder programming, download, and monitoring.
- The programming port used for program download and communication with the human machine
- This PLC adopts an industrial-grade 32-bit MCU with strong anti-interference, and its running speed far exceeds that of FX3U.
- This PLC transmission baud rate is 38400
LE3U PLC Manual
Test Video and Plc Program Example
- LE3U PLC analog test with op320
- LE3U PLC And computer communication
- LE3u connect computer BY GX Develop
- LE3u connect computer BY GX Work2
- LE3U and op 320 by 485 setting
- LE3u connect TK6070 hmi
- LE3U PLC AB phase encoder
- LE3u power off hold
- PID test programming
- LE3U D8120 setting
- Install GX develop software
- *Ethernet module + FX3U series PLC
- LE3u PLC connect samkoon hmi
- LE3U plc analog test
- LE3U plc Latch memory
- How to Connect Fx3u plc with Weintek hmi
- How to read Temperature with Ntc Thermistor
LE3U PLC WIRE
DB9 connector pinout
2 (Rxd), 3 (Txd), 5 (GND) pin
1. DC+ 24V power supply input positive pole
2. DC- 24V power supply input negative pole
3. Com Input common, low level
4.What is ” JO” CAL & CAH ?
CAN function is temporarily not supported
5.The working principle of RS485 communication is as follows:
Our le3u series PLC support MODBUS-RTU
LE3U PLC Connect MCGS HMI
LE3U PLC Upload and Download
Do not connect with rs232c
Must be create new project, not load project from PLC
AD and DA I can do input and output how to read and write
- Any example PRG with FB in MAIN POUNow Plc don’t support FB
- if LE3U support MODBUS Read/Write Instruction “ADPRW”sorry ,don’t support
- LE3U PLC with MCGS HMILE3U PLC and MCGS HMI Connect Setting Example
- GX-Developer-8.50C-E errorBecause the pathname of the installer folder is too long installation processing is discontinued.Please move the installer folder to the place which … Read more
- LE3U set to power off a range of D registerD0 to D511 do not hold by default, and D511 holds by default. So when programming, pay attention to the allocation of … Read more
- LE3U PLCContents1 LE3U PLC Manual2 Test Video and Plc Program Example3 LE3U PLC WIRE4 LE3U Cell5 DB9 connector pinout6 LE3U FAQ7 LE3U PLC … Read more